PS-18 and 19 to
PS-16 to case
PS-12 to case
PS-11 to case
100 to 150
Voltage regulator assembly
CR-2 to CR-18
Less than 1
(Generator set, serial num-
bers 923-001 thru 923-553)
CR-18 to case
45 to 50
CR-18 to CR-5
10 to 15
Inspection and Repair.
(Serial numbers 923-001 thru 923-553
(1) Inspect voltage regulator assembly for electrical continu-
ity as described in electrical troubleshooting (para. 4-9) .
regulator assembly if defective.
(2) Check external connectors for evidence of damage to
threads, pins, and sockets.
Replace connectors if damaged.
(3) Inspect cover, case, and base plate for deep dents and
distortion of surfaces.
Replace components that show either of
(4) Check relay assembly, voltage regulator assembly, and
cable assemblies for burned, worn or frayed insulation.
components that show any one of these defects.
screws and threaded parts for crossed, worn, or
Rep1ace parts if damage is beyond repair.
Repair of the generator components consists of re-
placing parts that do not pass visual inspection and have not retained