Figure 2-7. Compressed air and vacuum connection and control panel.
Section II. MOVEMENT TO A NEW WORKSITE
2-4. Dismantling for Movement
Disconnection of Accessory Components.
Disconnect all electrical cable assemblies (fig. 1-16) from receptacles on electrical output connection panel
and remote power connection panel (fig. 2-3) and from other elements of the MUST hospital. Coil cable assemblies and
secure ends for stowage. Remove ground wire from electrical system ground terminal (fig. 2-3). Close or install all
protective covers on receptacles of electrical output connection panel and remote power connection panel (fig. 2-3).
Disconnect all conditioned air duct assemblies from return air inlets (fig. 1-1) and conditioned air outlets
(fig. 1-2). Install covers over air inlets and outlets and secure covers with clamps. Visually inspect duct assemblies for
abrasions, holes, or other damage. Separate conditioned air duct assemblies (fig. 1-16) from conditioned air duct
coupling assemblies (fig. 1-16), collapse duct assemblies, and secure in the collapsed position with duct retaining
Handle conditioned air duct assemblies with care to avoid damage to fabric.
Close hot and cold water valves (fig. 2-6). Disconnect dual water hose assembly (fig. 1-16) and supply and
drain water hose assembly (fig. 1-16) from water inlet and outlet connection panel (fig. 1-1) and from water supply and
discharge points. Drain hose assemblies. Coil hose assemblies and secure ends for stowage. Drain power unit water
system as follows.