(7) Orientation Instructions. When con-
structing the revetment, the orientation of the
structure will be such that its entrance will face the
prevailing wind (fig. 4-1). The generator will be
centered within the revetment and will be posi-
tioned so that the long axis of the generator set is
parallel to the long axis of the revetment. In addi-
tion, the generator end of the generator set will be
positioned next to the entrance. These instructions
are very important and will be observed so that
proper cooling and ventilation will be obtained
when the unit is operated in a revetment.
(8) Multiple-Unit Installation. No more
than one generator set will be operated in a re-
vetment. Also, no other heat generating equipment
will be placed in a revetment with a generator set.
4-3. Equipment Conversion.
For conversion of the generator set to a different
voltage or phasing requirement, refer to figure 2-4
and to table 4-1.