This section contains troubleshooting informa-
for locating and correcting operating troubles
which may develop in the generator set. Each
malfunction for an individual component, unit, or
system is followed by a list of tests or inspections
which will help you to determine probable causes and
corrective actions to take. You should perform the
tests/inspections and corrective actions in the order
b. This manual cannot list all malfunctions that
may occur, nor all tests or inspections and corrective
actions. If a malfunction is not listed or cannot be cor-
rected by listed corrective actions, notify organiza-
tional maintenance personnel.
3-8. Operators Troubleshooting
Refer to table
3-4 for troubleshooting procedures.
Before you use this table, be sure you have
performed all applicable operating checks.