Table 3-2. OPERATOR/CREW PREVENTIVE MAINTENANCE CHECKS AND SERVICES
CHECK FOR HAVE REPAIRED
OR ADJUSTED AS NECESSARY
Visually inspect the generator set for
Class III oil or Class I
fuel and oil leaks
fuel leak is detected.
Check engine oil level. Add od as
Check for proper ground connection.
Generator is not prop-
.Inspect for loose, damaged, or missing
Any loose, damaged.
parts and unusual wear or deterioration
or missing parts: (i.e.,
Clean unit as necessary.
spark plugs, man-
ifolds, starter, or other
Insure load terminal wires are tight-
Loose load terminal
Check battery for tight terminals and
Unserviceable or loose
battery terminals and
Visually inspect all controls for ser-
Loose wire connec-
viceability before starting generator
tions or broken meter
Inspect for cracked or broken welds.
Instruments shall indicate within speci-
fled limits (para 2-1).
Fequency cannot be
Start generator after visual PMCS; insure generator operates as stated in paragraph 2-1.
3-4 Change 10