T M 5 - 6 1 1 5 - 3 3 2 - 1
P - 8 - 6 1 4 - 1
3 5 C 2 - 3 - 4 2 4 -
Table 8-1. Visual and Operational Inspection (Cont'd)
9 . G e n e r a t o r
a. Generator must be securely mounted and the rotor exciter
shaft securely attached to the flywheel.
b. During operation,
there shall be no excessive noise or
c. Conduct u Ioad test to insure that the set is operable and
that all meters are functioning properly.
d. Output should be in accordance with specifications.
e. W i r i n g t e r m i n a l s s h a l l be clean, wiring will not be burnt.
chafed, broken, cracked, cut or bare.
grease, oil, and corrosion,
g. Switches and contacts shall not be burnt, corroded or show
signs of wear.
h. No excessive end play or vibration of rotor shaft is allowed.
replace bearing i f necessary.
i. Frames shun not be crocked or broken.
j. There shun be no missing or loose parts.
k. The exciter rotor, stator, main rotor and stator, shall be free
of any obvious or visually apparent defects. Apply a dielectric in-
sulation or megger test when deemed necessary.
All interference suppression components shall be installed and
11. Skid Base, Frame and Components
a. The frame and supports shall he securely attached, and
shall support the generator and engine without buckling when
raised, moved or skidded.
b. Welded parts shall he free from breaks or cracks at the
c. All mounting brackets shall be securely attached.
d. Paint shall be as specified for all components of the gener-