a. This section contains troubleshooting infor-
mation for locating and correcting most of the oper-
ating troubles which may develop in the generator
set. Each malfunction for an individual component,
unit, or system is followed by a list of test or in-
spections which will help you to determine the
probable causes and corrective actions to take. You
should perform the test/inspections and corrective
actions in the order listed.
b. This manual cannot list malfunctions that
may occur, nor all tests or inspections and cor-
rective actions. If
not corrected by
a malfunction is not listed or is
listed corrective actions, notify
4-15. Organizational Troubleshooting.
R e f e r t o t a b l e 4 - 3 f o r o r g a n i z a t i o n a
Before you use this table, be sure you have per-
formed all applicable operating checks.
4-16. General Instructions for use of
Introduction. In electrical troubleshooting,
the Simpson 160, the TS-352B/U, and the AN/URM-
105 will do the same job. Therefore, your shop sets
may contain any one of these multimeters (fig. 4-8).
Any of these three multimeters can be used to trou-
bleshoot your equipments electrical system. This
section shows how.
4 - 1