Table 11-1. Visual and Operational Inspection (Contd)
9. Radio Interference Suppression
All interference suppression components shall be
installed and securely fastened.
10. Frame and Components
a. The frame and shock mounts shall be securely
attached, and shall support the generator and en-
gine without buckling when raised, moved or
b. Welded parts shall be free from breaks or cracks
at the weld.
c. All mounting brackets shall be securely
d. Paint shall be as specified for all components of
the generator set.