Figure 9-5. Shock mount, removal and installation.
b. Cleaning. Clean shock mounts using a clean
cloth and dry low pressure compressed air.
c. Inspection and Repair. Inspect shock
mounts for cracks, breaks, chunking, dry rot or for
an oil soaked condition. Replace shock mounts as re-
(1) Position shock mounts in place on control
(2) Install rivets.
(3) Install shock mounts on control panel
mounting bracket in the same manner.
(4) Refer to paragraphs 9-8, 9-7, 9-6, 6-3, 4-29,
4-27, 4-25, 4-23, and 4-22 and install the rectifiers,
terminal board assembly, voltage regulator, control
panel, terminal load, voltage control switch, load
on/off switch, voltmeter, and rheostat.