ORGANIZATIONAL MAINTENANCE INSTRUCTIONS
Section I. SERVICE UPON RECEIPT OF EQUIPMENT
Inspecting and Servicing the Equipment
Make sure equipment is completely
deprocessed before servicing. Make
sure preservatives have been removed
from the crankcase and fuel filter.
Inspect the generator set thoroughly for
bent, cracked, or missing parts. See that all nuts and
bolts are in place and secure.
Inspect visible wiring for loose connections
and the wiring insulation for cuts, fraying and other
Inspect the unit to see that all protective
material and devices have been removed.
Lubricate the engine in accordance with
curat lubrication order. Refer to(LO 5-2805-259-12).
checks and services as listed in table 4-2.
When filling the fuel tank, do not
smoke or use an open flame in the
vicinity. Always provide a metal-to-
metal contact between the container
and the fuel tank. This will prevent a
spark from being generated as fuel
flows over metallic surfaces. Failure
to observe this warning may result in
death to personnel.
Do not fill the fuel tank while the
engine is running. Gasoline spilled
on a hot engine may explode.
Remove the fuel can adapter (fig. 4-1) and
fill the fuel can.