Table 9-1. Visual and Operational Inspection (Contd)
Generator must be securely mounted and the rotor exciter
shaft securely attached to the flywheel.
During operation, there shall be no excessive noise or
Conduct a load test to insure that the set is operable and that
all meters are functioning properly.
Radio Interference Suppression
All interference suppression components shall be installed and se-
Skid Base, Frame and
The frame, base pan, battery box and supports shall be se-
curely attached, and shall support the generator and engine
without buckling when raised, moved or skidded.
Welded parts shall be free from breaks or cracks at the weld.
All mounting brackets shall be securely attached.
Paint shall be as specified for all components of the generator