MAINTENANCE OF ENGINE AND ELECTRICAL, PANELS AND CONTROLS
Section I. ENGINE ASSEMBLY
The Military Standard Engine, Model
4A0843 is designed for general purpose use in industrial
For detailed maintenance of the engine,
refer to TM 5-2805-259-14, or TO 38G2-89-41.
Removal. Refer to paragraph 6-2 for
removal of the engine.
Cleaning and Inspection.
Clean all parts in a well-ventilated
area. Avoid inhalation of solvent
fumes and prolonged exposure of
skin to cleaning solvent. Wash
cleaning solvent (Fed. Spec. P-D-680
and P-S-661) used to clean parts is
potentially dangerous to personnel
and property. Do not use near open
flame or excessive heat. Flash point
of solvent is 100° F(38°C).
Clean housing with cleaning solvent,
Fed Spec. P-D-680 or P-S-661, and dry thoroughly.
Inspect for missing or damaged
hardware and replace missing or defective parts as
Installation. Refer to paragraph 6-2 and
install the engine.
Section II. CONTROL BOX
connections while the generator is
energized line. Failure to observe
this safety precaution may result in
severe electrical shock or death by
electrocution. The control box has a
hinged panel on which the gages and
instruments are mounted and which
opens to give excess to the interior
components of the control box.
Field Flash Switch
Removal. Refer to figure 7-1 or 7-2 and
remove the switch from the applicable model generator