pins 11 and 13. Repair open circuit and retest generator
for correct output. If battery
voltage is present at pins 11 and
13 of connector P4 but fails to
produce voltage, refer to field
Using a multimeter as a check
against the set voltmeter, test the
output terminals of the generator
set against all position settings of
the voltage selector switch.
Stop the generator set
and connect the load cables.
maintenance. Refer to figure 4-
67. Installation instruction: One
(750 ohms, 25 watts) must be
used with this regulator. For
connection of red, black and white
jumpers, see instructions on front
Removal. Refer to figure 4-67 and remove
the voltage regulator.
Change 8 4-76.1/(4-76.2 blank)